Payment & Shipping Terms:
|Product Name:||Y Strainer Valve||Pressure:||Medium Pressure|
|Standard:||API Standard||Body Material:||Cast Iron|
|Connection:||Flange Ends, RF||Color:||Blue,Customer's Request|
|Type:||Y Type Strainer.,Pipe Fittings||Meidum:||Water Oil Steam|
api y filter valve,
125lb y filter valve,
80mm y type strainer valve
Cast iron filters are widely used in metallurgy, chemical industry, petroleum, papermaking, medicine, food, mining, electric power, urban, household and other gas fields. Cast iron filter is an indispensable device on the transmission medium pipeline, usually installed at the inlet of pressure relief valve, pressure relief valve, positioning valve or other equipment, to eliminate impurities in the medium, in order to protect the normal use of valves and equipment, reduce equipment maintenance costs.
When the fluid enters the filter with a filter element, the impurities are blocked by the filter element, and the clean filter gas is discharged from the filter outlet. When it is necessary to clean, as long as the filter cylinder is disassembled, the filter element is taken out, and then it can be reloaded after cleaning. Therefore, the use and maintenance of cast iron filter is extremely convenient.
|Flange end||ANSI B16.1|
|Suitable temperature||temperature ≤ 200 ℃|
|Suitable pressure||pressure < 1.6 MPa.|
|Suitable medium||water oil steam|
|Body||ASTM A216 CL.B|
|Bonnet||ASTM A216 CL.B|
1. This product is kept in a dry warehouse and is strictly prohibited to be stored in the open air.
2. Long-term storage, regular maintenance.
3. The product is usually installed in the pressure relief valve, pressure relief valve, hydraulic control valve or the use of medium equipment at the inlet end.
4. Bypass the pipelines for installing the product.
5. The product should be installed from the distance of the protected valve should be 6 ~ 10 times the diameter of the protected valve.
6. When installing, the medium flow must be consistent with the direction of the arrow on the body.
7. When installing, the cover is under the diameter axis.
8. Pipe and valve cavity should be cleaned before installation.
9. Operating conditions should be consistent with the requirements in the main performance specifications.
10. Cleaning or cleaning should be carried out when the inlet and outlet pressure difference is greater than 0.2MPa.
This product is composed of body, cover, filter and other parts, the medium from the import into, through the filter screen filter, from the outlet out
Contact Person: Ms. Ada Chen