Payment & Shipping Terms:
|Product Name:||Water Conservancy Valve||Body Material:||Ductile Iron|
|Use:||Relief Pressure||Part Material:||Brass /ss304|
|Bonnet Material:||Ductile Iron||Temperature:||≤80℃|
Ductile Iron Water Pressure Relief Valve,
1.6mpa Water Pressure Relief Valve,
Ss304 Water Conservancy Valve
The 500 pressure relief/pressure holding valve is automatically operated by water, and can be used as both pressure relief valve and pressure holding valve. When used as a pressure relief valve, it can maintain the pressure of the water supply pipeline below the set safety value; When used as a pressure retaining valve, it can maintain the water pressure upstream of the main valve above the set value and maintain the water supply pressure upstream of the main valve. The operation system is stable, easy to maintain and repair. This valve is used in the fire protection system to prevent pipeline overpressure or maintain pipeline pressure. After the fire protection system is closed, it can also reduce the impact of water hammer. It is also used in high-rise buildings, living quarters water supply network systems and urban water supply projects.
|1.5MPA||2.4MPA||3.75MPA||Shell test pressure|
|1.1MPA||1.76MPA||2.75MPA||Seal test pressure|
500 pressure holding/relief valve is composed of main valve and pilot valve control system. The main valve is divided into upper valve cover control room and lower valve body flow channel. Needle valve, ball valve, pressure relief pilot valve, etc. are connected by copper pipes to form pilot valve control system. When the pilot valve is adjusted to the pressure relief state, the feed water at the inlet end of the valve flows to the outlet through the needle valve, bonnet control room, pressure relief pilot valve and ball valve. At this time, the main valve is in the open state. When the inlet pressure exceeds the safety value set by the pressure relief pilot valve, the pressure relief pilot valve will automatically open, the pressure in the bonnet control room will decrease, and the main valve will release pressure. When the pressure recovers to a safe value, the main valve automatically closes. When the pilot valve is adjusted to the pressure holding state, as long as the water pressure at the inlet of the main valve is lower than the set value of the pilot valve, the pilot valve will close. At this time, the pressure in the control room of the main valve will rise, and the main valve will close.
Contact Person: Ms. Ada Chen